Tools you will need:
Phillips screw driver
needle nose pliers
#14 awg wire
The function of the I33 cold control is to maintain bin (storage) temperature.
1.) Location of the I33 on model #85 and #84.
Rear view with back panels removed on both units.
2.) If units compressor and fan are inoperative and the ejection module (see section on I34M-1) is functional then place a temporary jumper across the two spade terminals (with the unit’s wiring intact) of the cold control.
If the compressor and fan operate the cold control is in need of replacement.